Specifications include, but are not limited to: Ceiling
Lay-in acoustical 2’ x 2’ tiles with suspended grid, with minimum NRC of 0.65.
Luna 2’ x 4’ recessed indirect light with narrow 4” perforated center basket fluorescent fixtures with energy efficient lamps (T-8 or better) and electronic ballasts shall be provided. Fixtures shall be capable of producing and maintaining a uniform lighting level of 50-foot candles at working surface height throughout the space. Indirect lighting to be suspended when ceiling height allows.
Restroom lighting shall be 30 foot candles measured at counter height and 20 foot candles measured at the floor in enclosed corridors.
Dimmable ballast fluorescent or zoned lights shall be provided for conference/training rooms and reception areas.
Emergency egress lighting as required by applicable life safety codes shall be provided throughout the entire space.
Gypsum wallboard, minimum thickness of 5/8” with studs at a maximum of 24” on center, level 4 finish.
Acoustical treatment in walls for all conference/meeting/training rooms, e.g. 3 ½” sound attenuation batt insulation.
Walls to be finished with primer and two finish coats of paint.
Movable Partition in training/conference room to be manually operated panels with 49/50 STC sound rating, vinyl finish over a steel face, manual floor seals and lever closure.
1” wide, metal blade mini blinds shall be provided and installed.
Flush solid wood core.
Minimum 3’-0” wide x 7’ high.