Specifications include, but are not limited to: Replacing the antiquated galvanized iron water distribution system with 2” and 3” CL160 PVC, replacing the galvanized iron intake pipe with 3” SDR9 PE, new water stands, concrete valve pits, concrete low point drains and improvements to the Pump House and Main Sewer Pump Station. For the Pump House, all existing galvanized piping, valves, fittings, pressure tank and air charging equipment, pumps (as indicated) and appurtenances will be removed and replaced with new SCH 80 PVC piping, new valves, and fittings, pressure tanks, pressure switches, pumps and wiring to the existing control panel. Also included is re-roofing the existing Pump House roof. For this portion, all existing shingles, underlayment, flashing, and drip edges shall be removed and replaced with new of the same, and any rotten sheathing will be replaced and the entire roof re-nailed. Renovation of the Main 4000-gallon Sewer Pump Station will consist of removing all existing pipe, valves, fittings, and bends will be replaced with SCH 40 PVC. The existing effluent pumps slide rail system, septic tank cover and riser, float control system and associated wiring, and appurtenances are to be removed and replaced with new pumps, slide rail system, pressure activated control system and associated wiring/tubing. The existing control and electrical pedestal will be rebuilt and a new control panel, electrical panel and hardware for generator hookup installed.