Specifications include, but are not limited to:
Water quality requirements are as follows:
SEMI Std. E49.7-0304
<20 ppb TOC
<5 Silicia (ppb)
<.1 CFU/ml or 10/100ml Bacteria
The system should be capable of producing at least 200 gallons per day with a pump to allow for building wide supply and recirculation at 30 ft. of head pressure with 600 linear feet of pipe. We need the system to be capable of connecting to our building automation systems and have a touch screen control panel. Power availability is 3 phase, 480 volts. We already have softening tanks and carbon filtration in place which has been replaced within the last year so that is not needed.