Specifications include, but are not limited to: Multiconductor control cable with shield, 600V for use in 345kV substation. The cable shall be
twelve (12) 10 AWG 7 strand, bare copper conductor with flame-retardant XLPE or EPR insulation and
polyvinyl chloride (PVC) or Chlorinated Polyethylene (CPE) jacket. Bare 5 mil corrugated copper tape
longitudinally applied shield. Suitable for utility company substation and power plant control
circuits and use in open air, ducts, trays, conduit or direct burial, indoors or outdoors. Rated at
90C wet or dry, sunlight, heat, flame, moisture and chemical resistant, would prefer low coefficient
of friction for pulling. Conductor colors to follow code Method #1 Table E1. Cable shall be supplied
on 1000FT non-returnable reels.