Specifications include, but are not limited to: The Contractor shall remove existing conductor bars.
The Contractor shall install replacement conductor bars with style that includes dedicated ground.
Replacement conductor bars will meet the existing conductor bar manufacturer’s specifications, to also include dedicated ground.
Grounded conductor and equipment grounding conductor must be identifiable and distinguishable from all other conductors.
The Contractor shall re-use as many existing conductor bar brackets as new application allows.
Conductor bar brackets that include curves and/or switches shall be replaced, as needed.
The Contractor will ensure the path to ground from circuits, equipment, and enclosures shall be permanent, continuous, and effective.
The system shall be installed in such a manner that its operation will not interfere with building operations.
The system shall be installed at the location specified in the diagrams.