Specifications include, but are not limited to: Only new material shall be used in the manufacturing process, and the manufacturer shall ensure that the material used meets all appropriate specifications and quality assurance requirements.
Nominal capacity of the Double Bulkhead tanks is listed below.
Two-hour fire rated, ballistics, impact and steam hose certified.
Minimal material thickness of the tank(s) shall be per UL-142 requirements.
Minimum annular space insulation thickness material shall be 3" with only UL-2085 listed insulation material.
Internal Load: Tank shall be able to withstand an air pressure test of 3 to 5 psi.
Tank shall be designed to support accessory equipment such as ladders, pumps, floating suction, etc. when installed according to manufacturer's instructions and limitations.
Tank(s) shall be provided with suitably designed and located lifting lugs which have a 2:1 safety factor.
NO Catwalk installed but shall be available at a future time.
Tank(s) shall be capable of storing liquids with a specific gravity up to 1.0.
Tank(s) is designed for operation at atmospheric pressure only. Both inner and outer tanks shall have openings of sufficient size to meet normal and emergency venting requirements stated in U.L. 142, UFC and NFPA.
Tank(s) shall be capable of storing gasoline and diesel fuel at ambient temperatures. ; Certification Plate: Underwriters Laboratories label "Insulated Secondary Containment Aboveground Tank for Flammable Liquids." shall be affixed to each tank.