Specifications include, but are not limited to: Contact J.U.L.I.E. at 1 / 800 – 892 – 0123 within fourteen (14) days prior to directional boring of new water line, to locate existing water line, and mark its present location, and any other utilities present.
Directional bore a new 3/4-inch type K copper water line alongside existing water line. New line is to be buried below frost line, a minimum of 48 inches below grade.
Connect new water line to existing pipe and existing tap inside building envelope; provide new brass ball shut-off valve and system drain down in basement. Shut-off valve shall comply with City of Galena plumping code requirements -- the City of Galena has adopted the 2014 Illinois State Plumbing Code. Connect new line to existing pipe near water main located near street. Total run is approximately 125 feet (Plumbing Contractor to verify). Existing line to be abandoned in place within the building envelope; Contractor shall use existing building penetrations. See attachment of City of Galena sketches. Contractor shall comply with City of Galena and Department of Public Health plumbing code requirements.