Specifications include, but are not limited to: Water Tank
The water tank shall be constructed of 1/2" thick polypropylene sheet stock with PolymarCo-PP™
resin. Water tank shall be welded with Heavy Duty extruded joint. The material shall be of a
certified, high quality, non-corrosive, stress relieved thermo plastic, black in color with a textured
finish, and UV stabilized for maximum protection. The skid type water tank shall be of a standard
configuration and shall be so designed to have complete modular slide in capability. The unit
shall incorporate transverse partitions manufactured for 3/8" PT2E polypropylene which shall
interlock with a series of longitudinal partitions constructed of 3/8" PT2E polypropylene. All
swash partitions shall be so designed to allow for maximum water and air flow between
compartments and are fully welded to each other as well as to the inside of the tank.
The passenger side rear wall of the tank shall have a standard built in sight gauge 3" in width, and
The tank shall be equipped with a combination vent/overflow and manual fill tower. The fill
tower shall have a 8" x 8" x 8" square drop-on type cover. The cover shall be fastened to the
tower with a tether to prevent loss. The tower shall be located in the right rear corner of the
tank. There shall be a vent/overflow installed inside and to the extreme rear of the tower
approximately 2" down from the top. This vent/overflow shall be of a standard schedule 40
polypropylene pipe with minimum ID of 3". The vent/overflow shall be piped internally toward
the front and exit out the front tank wall with a 1/2" extension past the front tank wall. The tank
cover shall be constructed of 1/2" thick PT2E polypropylene, black in color, UV stabilized.
Tank will be baffled with Finger-Loc baffling system that exceeds NFPA 1901, latest version.
The tank shall have a capacity of 300 U.S. gallons of water. The tank shall be covered by an ALL
OUT No Fault Life Time Warranty.
In addition, a 10 gallon Drop-in integrated foam cell will be included. A label that reads “Foam”
shall be placed at any foam concentrate tank fill opening.
The floor of the tank shall be manufactured from 3/4" PT2E polypropylene. There shall be one
(1) sump as standard per tank. The sump shall be integral to the tank floor and be a minimum of
3/8" deep recessed into the floor. The sump shall not be visible from or protrude through the
bottom of the tank.
There shall be two standard tank outlets located in the same vertical plane on the driver’s side
rear wall of the tank. One (1) 2 1/2" female NPT tank to pump suction fitting and one (1) (1”)
female NPT tank fill fitting with flow deflector