Specifications include, but are not limited to: The City of Redlands Municipal Utilities and Engineering department (City) is currently soliciting bids from vendors to provide Mill Creek #2 Well Repair. Mill Creek 2 Well is a water lubricated cable tool well. The well has a 20” casing and is 271’ deep, the pump setting is 230’. This well is a crucial water source for Mountain Home Village. The well is one of two water sources for this town, so down time needs to be kept very minimal. Some emergency work was preformed last year. The bowl assembly was replaced, new bronze drop in retainers with Vesconite bushings were installed, the foot valve was removed and 20’ of slotted suction was added to help with possible sand issues. The equipment was put back into service in May of 2018. The well has recently developed a vibration and will need to be pulled for an inspection and repair. A sand test was performed recently with minimal sand found. Last year a video log and brush and bail was performed because of that, no well casing rehab work will be needed at this time.