Specifications include, but are not limited to: 1. Monitoring Shelter: One (1
Shelter Dimensions: 8’L X 8’W x 8’H (at a minimum).
Two (2) Aluminum skid base plates with fork-lift lifting points. The plates should run
length-wise along the shelter and should be mounted 18 inches on center from the
edge of the shelter.
Aluminum exterior skin including trim.
Rust proof fasteners
Rubber membrane roof
Titanium dioxide waterproofing agent (or equivalent).
Insulation in walls, ceiling, and floor shall be R-25 equivalent.
Stud-less wall construction
Seamless vinyl flooring (slip resistant).
Fiberglass reinforced panel interior finish (white).
Insulated metal access door (36”), includes hydraulic door closer, weather stripping,
door drip shield, door threshold, and handle with lock.
2. Electrical System
Meets or exceeds NEC regulations.
100A 1PH 120/240V Electrical System.
100A 1PH 120/240V Load Center.
100A 1PH 240V External Disconnect, Nema 3R.
Electrical Surge Protection for System.
Metal Electrical Raceway
Three (3) 120V 20A duplex interior receptacles.
Two (2) 48” double bulb fluorescent light fixture w/ switch.
Two (2) External 120V 20A GFCI Outlets on separate circuit breakers for roof.