1.1. This specification covers 15kV single conductor shielded primary cable.
1.2. The cable is suitable for single- or three-phase applications for installation in underground
ducts, conduits, or direct burial in wet locations.
1.3. The cable shall be rated 90˚C for normal operation, 130˚C for emergency overload operation,
and 250˚C for short circuit conditions. Emergency overload operation may occur for periods
up to 1500 hours cumulative during the lifetime of the cable.